When designing and building a basement wall using spray foam insulation you need to take into account code related to:
Vented Crawl Space Code
Local codes based on IRC 2009: Section N1102.2.7
Local codes based on IRC 2012: Section N1102.2.8
Spray Foam Code
Local codes based on IRC 2009: Section R316
Local codes based on IRC 2012: Section R316
Building Thermal Envelope Code
Local codes based on IRC 2009: Section N1102
Local codes based on IRC 2012: Section N1102
To find out which code your local code is based on, go to http://bcap-ocean.org/code-status-residential.
Do I Need a Thermal Barrier?
In an occupied space, you need a thermal barrier adjacent to either low density or medium density foam - this could be ½ inch gypsum board, or a code-prescribed barrier per R316.4, depending on the spray foam section of your local code. See each Icynene spray foam product to check which paint-on or spray-on thermal barriers can be used.
If the space is unoccupied, you don't need a thermal barrier.
Do I Need an Ignition Barrier?
In an unoccupied space, you need an ignition barrier adjacent to either low density or medium density foam - this could be an intumescent paint, or from the list in R316.5.3, depending on the spray foam section of your local code. See each Icynene spray foam product to check which paint-on or spray-on ignition barriers can be used.
Do I Need a Vapor Barrier?
This depends on your local code requirements; it’s affected by climate and the elements in the building envelope.
What R-value Do I Need?
This depends on your local building thermal envelope code requirements.
ICC code allows Icynene spray foam insulation to be installed with less than the prescriptive minimum R-value and still meet the intent of the code.
Compliance based on simulated energy performance requires that a proposed residence (proposed design) be shown to have an annual energy cost that is less than or equal to the annual energy cost of the standard reference design that is based on the minimum prescriptive standard. When the air tightness of the building envelope is factored into the computer calculations, the building will require less R-value than the prescriptive level mandates. Typically the R-value can be reduced by 20-25%, depending on the code version that is being used. Icynene may be able to help with REM/Design analysis.
2006 IECC Chapter 4 Section 404.3 - Performance-Based Compliance
2009 / 2012 IRC N1105 - Performance-Based Compliance
Get Answers to Spray Foam Code Questions for Your Project
Contact Icynene Customer Service at 1-800-758-7325 begin_of_the_skype_highlighting 1-800-758-7325 FREE end_of_the_skype_highlighting or email email@example.com for more detailed help to find answers on these code requirements for your project. Many factors affect code requirements for a project, and we’d be happy to find the right expert to discuss your situation and local codes.